An a/c unit's filters, coils, and fins need routine maintenance for the system to function successfully and efficiently throughout its years of service. Disregarding required upkeep ensures a consistent decline in a/c efficiency while energy usage progressively increases. Take a look at our Energy Saver 101 Infographic: Home Cooling for more methods to help enhance your comfort and the efficiency of your a/c.
Air Conditioning Unit Filters
The most essential upkeep task that will ensure the effectiveness ΕΠΙΣΚΕΥΗ ΚΛΙΜΑΤΙΣΤΙΚΩΝ ΑΘΗΝΑ of your a/c unit is to routinely change or clean its filters. Obstructed, unclean filters obstruct typical airflow and lower a system's performance significantly. With normal air flow blocked, air that bypasses the filter may carry dirt directly into the evaporator coil and hinder the coil's heat-absorbing capability. Replacing a dirty, stopped up filter with a tidy one can lower your a/c's energy consumption by 5% to 15%.
For central air conditioning conditioners, filters are usually situated somewhere along the return duct's length. Typical filter places are in walls, ceilings, furnaces, or in the air conditioner itself. Space air conditioning unit have a filter installed in the grill that deals with into the space.
Some kinds of filters are multiple-use; others must be replaced. They are readily available in a variety of types and effectiveness. Tidy or replace your cooling system's filter or filters on a monthly basis or two throughout the cooling season. Filters might require more frequent attention if the a/c is in continuous use, goes through dusty conditions, or you have fur-bearing family pets in your home.
Ac System Coils
The air conditioning unit's evaporator coil and condenser coil collect dirt over their months and years of service. A clean filter prevents the evaporator coil from soiling rapidly. In time, nevertheless, the evaporator coil will still gather dirt. This dirt lowers air flow and insulates the coil, reducing its capability to take in heat. To prevent this issue, check your evaporator coil every year and tidy it as needed.
Outdoor condenser coils can likewise become really dirty if the outdoor environment is dirty or if service klimatistikon athina there is foliage close by. You can quickly see the condenser coil and notice if dirt is gathering on its fins.
You ought to decrease dirt and debris near the condenser system. Your clothes dryer vents, falling leaves, and mower are all possible sources of dirt and debris. Cleaning the area around the coil, getting rid of any debris, and cutting foliage back a minimum of 2 feet (0.6 meters) permit appropriate airflow around the condenser.
The aluminum fins on evaporator and condenser coils are easily bent and can block airflow through the coil. Cooling wholesalers offer a tool called a "fin comb" that will comb these fins back into nearly initial condition.
Condensate Drains pipes
Occasionally pass a stiff wire through the unit's drain channels. Blocked drain channels avoid a system from decreasing humidity, and the resulting excess wetness might blemish walls or carpet.
Window Seals for Room Air Conditioners
At the start of each cooling season, inspect the seal in between the air conditioning unit and the window frame to guarantee it makes contact with the unit's metal case. Wetness can damage this seal, enabling cool air to escape from your home.
Getting ready for Winter
In the winter, either cover your space a/c unit or eliminate and keep it. Covering the outside system of a central air conditioning conditioner will safeguard the system from winter season weather and debris.
Employing a Specialist
When your a/c requires more than regular maintenance, work with a professional service specialist. A trained professional will find and fix problems in your cooling system.
The service technician needs to:
Check for correct quantity of refrigerant
Test for refrigerant leakages using a leak detector
Capture any refrigerant that needs to be evacuated from the system, instead of unlawfully launching it to the environment
Check for and seal duct leak in central systems
Procedure air flow through the evaporator coil
Verify the right electrical control series and make sure that the heater and cooling system can not operate concurrently
Check electrical terminals, clean and tighten connections, and apply a non-conductive coating if essential
Oil motors and inspect belts for tightness and wear
Inspect the precision of the thermostat.