An air conditioning system's filters, coils, and fins require regular maintenance for the unit to work successfully and effectively throughout its years of service. Ignoring essential upkeep guarantees a consistent decline in air conditioning efficiency while energy usage gradually increases. Check out our Energy Saver 101 Infographic: Home Cooling for more ways to help enhance your convenience and the efficiency of your air conditioning unit.
Ac System Filters
The most essential upkeep task that will guarantee the effectiveness of your a/c is to regularly replace or clean its filters. Blocked, filthy filters obstruct normal air flow and reduce a system's performance substantially. With typical airflow obstructed, air that bypasses the filter may carry dirt directly into the evaporator coil and impair the coil's heat-absorbing capacity. Changing an unclean, blocked filter with a tidy one can decrease your a/c unit's energy usage by 5% to 15%.
For central air conditioners, filters are usually located somewhere along the return duct's length. Common filter locations are in walls, ceilings, furnaces, or in the air conditioner itself. Space air conditioners have a filter mounted in the grill that deals with into the room.
Some types of filters are multiple-use; others should be replaced. They are offered in a variety of types and efficiencies. Clean or change your air conditioning system's filter or filters on a monthly basis or two during the cooling season. Filters may require more regular attention if the ac system remains in constant usage, undergoes dirty conditions, or you have fur-bearing pets in your house.
The ac system's evaporator service klimatistikon athina coil and condenser coil gather dirt over their months and years of service. A tidy filter prevents the evaporator coil from soiling quickly. In time, however, the evaporator coil will still gather dirt. This dirt reduces airflow and insulates the coil, lowering its ability to absorb heat. To avoid this problem, inspect your evaporator coil every year and tidy it as required.
Outside condenser coils can also become very unclean if the outside environment is dusty or if there is foliage nearby. You can easily see the condenser coil and notice if dirt is gathering on its fins.
You must reduce dirt and debris near the condenser system. Your dryer vents, falling leaves, and lawn mower are all possible sources of dirt and debris. Cleaning up the area around the coil, getting rid of any particles, and cutting foliage back a minimum of 2 feet (0.6 meters) allow for adequate air flow around the condenser.
The aluminum fins on evaporator and condenser coils are easily bent and can block air flow through the coil. A/c wholesalers sell a tool called a "fin comb" that will comb these fins back into nearly initial condition.
Condensate Drains pipes
Sometimes pass a stiff wire through the unit's drain channels. Obstructed drain channels prevent an unit from reducing humidity, and the resulting excess wetness may blemish walls or carpet.
Window Seals for Space Air Conditioners
At the start of each cooling season, check the seal between the a/c unit and the window frame to guarantee it makes contact with the system's metal case. Moisture can harm this seal, permitting cool air to get away from your house.
Preparing for Winter
In the winter season, either cover your space ac system or remove and store it. Covering the outdoor unit of a central air conditioner will protect the system https://www.washingtonpost.com/newssearch/?query=ΕΠΙΣΚΕΥΗ AIR CONDITION from winter season weather condition and particles.
Hiring a Specialist
When your air conditioning unit needs more than regular upkeep, work with a professional service specialist. A trained technician will find and fix problems in your air conditioning system.
The technician ought to:
Look for appropriate amount of refrigerant
Test for refrigerant leaks utilizing a leakage detector
Record any refrigerant that must be left from the system, rather of unlawfully releasing it to the environment
Look for and seal duct leak in central systems
Measure airflow through the evaporator coil
Validate the right electrical control series and ensure that the heating unit and cooling system can not run at the same time
Check electric terminals, tidy and tighten up connections, and use a non-conductive coating if necessary
Oil motors and inspect belts for tightness and wear
Check the accuracy of the thermostat.